What is the base of your irrigation system?
Order within 0hrs 0mins for same-day shipping!
*Not available with backorder/drop-ship items. See Shipping Policy
Creative Sensor Technology introduces a new technologically advanced flow sensor designed spe- cifically for the irrigation industry.
The sensor features a square wave digital signal proportional to flow. The charac- teristics of the output signal duplicate existing impel- ler flow sensor signals making the FSI series sensor compatible with all manufacturer’s control products. The pulse signal will travel up to 2,000 feet without amplification.
The key elements of this new technology are a proprietary mounting tee, ultra-lightweight impeller and improved processor based electronics giving the FSI series sensor improved performance.
Always install a flow sensor in a straight section of pipe where there is a minimum of 10 diameters upstream (ahead) and a minimum of 5 diameters downstream (behind) of the flow sensor. Pipe bends, other fittings, valves, pipe enlargements or reductions or anything else that would cause a flow disturbance should not be present in this length of pipe.
If the flow sensor is installed below grade, provide access to the sensor by installing a valve box or meter pit over it. In underground installations, sensor tees are usually installed with the insert located in the 12:00 o’clock or straight up position to make removal easier. The sensor
is supplied with 48” wire leads. When splicing the leads to an extension cable, be sure to leave an adequate loop of wire to allow the sensor insert to be brought above ground level for service while still remaining spliced.