Order within 0hrs 0mins for same-day shipping!
*Not available with backorder/drop-ship items. See Shipping Policy
Reduces pipe banging caused by water hammer. All copper and brass external construction. Air chamber is permanently sealed. Designed to protect residential, commercial and industrial water lines during pressure surges following quick valve closure. This excessive pressure surge is absorbed by the pre-charged cushion of air permanently sealed within the water hammer arrester. The water hammer arrester may be installed within a stud bay without the need for an access panel.
Rule 1 - Branch lines of 20 feet or less.
Water Hammer Arrester should be placed at the end of the branch line between the last two fixtures served, as shown at right. Select required model using fixture unit sizing.
Rule 2 - Branch lines exceeding 20 feet.
An additional Water Hammer Arrester should be placed as shown at right. Select required models using fixture unit sizing. The sum of the fixture unit ratings of units X and Y shall be equal to or greater than the demand of the branches.
When long runs of piping are employed to serve a remote item of equipment, the Water Hammer Arrester should be located as close as possible to the point of quick closure (see Fig. 4).
The size and quantity of Water Hammer Arrester to be installed in branch lines is shown in Table III. Ideally, the flow pressure in branch lines serving fixtures should never exceed 55 PSIG. Pressure reducing valves should be installed to maintain proper pressure. When, however, flow pressures of 65 to 85 PSIG are used, the next larger size Water Hammer Arrester should be selected (see Table III).