Designed for installation on potable water lines to protect against back siphonage of contaminated water into the potable water supply. Assembly shall provide protection where a potential health hazard exists.
The Pressure Vacuum Breaker shall be ASSE 1020 approved, and supplied with full port ball valves. The main body and bonnet shall be bronze (ASTM B584), the loaded-air inlet shall use a silicone elastomer spring and seat disc. The entire assembly shall be accessible for maintenance and testing without removing the device from the line. The Pressure Vacuum Breaker shall be a WILKINS Model 720A.
Local codes shall govern installation requirements. Unless otherwise specified, the assembly shall be mounted at a minimum of 12" (305mm) above the highest piping or outlet downstream of the device.
Install with adequate drain and sufficient side clearance for testing and maintenance. The installation shall be made so that no part of the unit can be submerged. A pressure vacuum breaker cannot be installed where back-pressure could occur or where spillage of water from the vent could cause damage.
|Test Cocks||2 FEMALE|
|Max Working Pressure||150 PSI|
|Hydrostatic Test Pressure||300 PSI|
|Temperature Range||32F to 110F|
|Main Valve Body Materials||Bronze|
|Lead Free||Not Lead Free|